- Wiring Bulletin - Grounding electrode conductor must terminate at the neutral bar in the service.
- NEC 110.24 requires service equipment in other than dwelling units to have the available fault current labeled. The label shall have the date the calculation was figured and shall be able to withstand the environment involved.
- NEC 408.4 - Labeling breakers
- Size over current protection per name plate on equipment. Example air conditioner.
- NEC 406 Install weather resistant receptacles.